Cable, Power Cable, N2xsy Cable manufacturer / supplier in China, offering N (A) 2xs (E) Y XLPE Power Cable, H07V-U H05V-U H07V-R 1.5mm 2.5mm Electric BV Kabel PVC Building Wire, 450/750V Low Voltage PVC Electric Copper Building Wire Zr-BV/BVV//Bvr/RV/Rvv Kabel Wire and so on.
|Min. Order / Reference FOB Price||1,000 Meters||US $5/ Meter|
|Payment Terms:||L/C, T/T, D/P, Western Union, Paypal, Money Gram|
|Conductor Material:||Copper or Aluminium or Aluminium Alloy|
1,Long term working temperature for the cable with PVC insulated is 70ºC;
Long term working temperature for the cable with XLPE insulated is 90ºC
2,Short circuit temperature
For PVC insulated cable ,the highest conductor temperature is not more than160ºC.(lasting time not over 5 seconds).
For XLPE insulated cable ,the highest conductor temperature is not more than250ºC.(Lasting time is not over 5 seconds).
3,Laying temperature not less than 0ºC and the drop height is out of consideration.
4,The cable with chemical stability, anti- acid, anti-alkali, anti-oil, anti-organic solvent, not easy to be burning.
5,Easy for installation, easy bending and light
Min bending radius during installation
Near joint box or cable terminal, bending with care and use templet
Note:D is the diameter of cable
Rated Voltage :0..6/6kV,3.6/6kV.
Conductor of cables can be Copper and Aluminum. The cables can be single core, two cores, three cores, four cores(including three main cores and neutral).five cores (including three main cores and neutral and one earthing core, Four main cores and one neutral).The cables can be with armor and without armor.
Rated voltage 6kV (Um=7.2) and 35kV (Um=40.5)
XLPE insulated cable has good electrical and physical properties, resistant to aging, resistant to the environment stress and chemical corrosion operation, with the characteristics of simple structure, easy to use, no drop-height restriction when laying, higher long-term working temperature (90ºC).
Category A ,B
Category A ,B
The cable with Category A rated voltage is used in the situation requiring not over 1 min. of grounding fault lasting time. For the cable with Category B rated voltage, the grounding fault lasting time normally is not over 1 hour, max. lasting time is not over 8 hours, annual ground fault lasting time altogether should not be over 125 hours, Category C includes all the system expect Category A and B.
|Number of cores and cross-section||Shape of conductor||Conductor diameter||Nominal insulation thickness||Diameter over insulation||Nominal thickness sheath||Outer diameter (approx.)||Bending radius (min.)||Weight (approx.)|